The pendant and wall mount emergency stop buttons function identically, and any e-stop button will stop both arms. The buttons are locking, push to operate, twist to release.
Emergency stop functions independently from the other safety interlocks.
After an e-stop event, the e-stop button involved must be released and the RESET button on the interlock panel must be pressed to reset the e-stop relays.
Power Up Initialization
After a power interruption to the interlock control panel, the RESET button on the interlock panel must be pressed to reset the e-stop relays.
Both controllers are enabled in parallel. Manual and automatic modes may be enabled simultaneously, so, for example, one arm may be operated manually while the other is computer controlled.
To enable manual operation, turn the key switch on the interlock panel to MAN ENABLE. To disable manual mode, return the key switch to its center position.
To enable automatic operation, all door interlocks must first be closed. Momentarily turn the key switch on the interlock panel to AUTO ENABLE and release. An audible alarm will sound and the strobe will flash for a preset delay. After the delay the strobe will go to solid on and the controllers will be enabled for computer control.
To disable automatic mode, either press the RESET button on the interlock panel or open one of the doors. To disable manual mode, return the key switch to its center position.
The swinging door must be completely closed to close its interlocks.
The sliding door must be either completely closed, or opened to its four-inch detent, to close its interlocks.
The sliding door interlocks may be overridden by plugging a closed contact into the 1/4" jack under the SLIDING DOOR OVERRIDE led. This is intended for use by a safety observer holding a kill switch.
The entire interlock system may be overridden by turning the key switch under the OVERRIDE ALL led. Interlock override has no effect on emergency stop functionality.